Two Conductor Aluminum Jacketed MC Cable and Grounding Conductor 600V
Applications MC Cable is approved for use in many applications including direct burial, use in cable tray and outdoor exposure. The PVC jacket is free of harmful heavy metals in compliance with RoHS, Directive 2002/95/EC. Run from the combiner box to the inverter Suitable for rooftop solar applications Outdoors In wet locations (Type XHHW-2 , or RHW-2 conductors) Direct buried Encased in concrete Hazardous locations Strong, but lightweight alloy armor resists damage Suitable for wet locations, direct burial, encased in concrete and other uses per the NEC More flexible than conduit Factory tested engineered product that protects conductors from damage during installation Meets or exceeds requirements of the NEC, as well as applicable UL Standards. Specifications Single conductors are rated XHHW-2, and CT Use 1/0 AWG and larger Aluminum armor is rated for Direct Burial, using 6 AWG and larger conductors, with overall jacket Approved for use in certain hazardous locations as permitted in Articles 501, 502, 503 and 504 UL 1569, Metal Clad Cables UL 44, Rubber-Insulated wires and cables ICEA S-95-658 Standard for Non-shielded Power Cables Rated 2000 volts or less Construction Stranded Aluminum alloy (AA8000) compacted conductor, Class B stranding, per ASTM B 801. Flame retardant thermoset crosslinked polyethylene (XLPE) insulation. Grounding is one bare aluminum alloy (AA-8000)compacted stranded conductor.