Duplex Conductor 600V Secondary Type URD Cable - Aluminum Conductor
Applications Directly buried or installed in ducts for 600 volt secondary distribution. Construction Concentric stranded or compressed 1350-H19 aluminum conductor, crosslinked polyethylene insulation. Insulated conductors surface printed, neutral triple yellow striped. Black neutrals may be specified if desired. Standards Secondary URD duplex conductor 600V cable meets or exceeds the following ASTM specifications. B-230 Aluminum Wire, 1350-H19 for Electrical Purposes. B-231 Aluminum 1350 conductors, Concentric-Lay-Stranded. B-786 ""19 Wire combination unilay-stranded Aluminum Conductors for subsequent insulation"". B-901 ""Compressed round stranded Aluminum Conductors using single input wire construction"". Secondary UD duplex conductor 600V cable meets or exceeds all applicable requirements of ICEA S-105-692. ""USE-2"" per UL 854 available upon request. Options Cable in Duct Abrasion Resistant Ampacity 90ºC conductor temperature, 20ºC ambient, RHO 90, 100% load factor. All yellow extruded stripe cable is XLP insulation. To determine correct ampacity by conductor size, please consult the National Electric Code, latest edition.